Although high pressure medical oxygen filling systems are not fully consistent with the principle of on-site oxygen production, in certain situations it might be interesting to fill oxygen cylinders to serve as a back-up supply.
Indeed, on-site oxygen production is designed to safely produce oxygen at low pressure and directly feed the medical oxygen piping system of the hospital. The interest is to avoid the manipulation of dangerous high pressure oxygen cylinders. However, it is mandatory for an hospital to have three sources of oxygen supply, hence it is possible to consider high pressure filling systems in order to refill fixed oxygen cylinders as second or third source of oxygen for the hospital.
GAZ SYSTEMES has a range of pneumatic oxygen boosters which are reliable and are powered using the same compressor than for the PSA oxygen plant. Pneumatic technology allows low rpm with less maintenance and high life expectancy.
|Models||Oxygen flow*||Max outlet pressure|
|OxyBOOST 20||2 m3/h||150-200 bar|
|OxyBOOST 40||4 m3/h||150-200 bar|
|OxyBOOST 60||6 m3/h||150-200 bar|
|OxyBOOST 80||8 m3/h||150-200 bar|
|OxyBOOST 120||12 m3/h||150-200 bar|
|OxyBOOST 180||18 m3/h||150-200 bar|
|OxyBOOST 240||24 m3/h||150-200 bar|
|OxyBOOST 360||36 m3/h||150-200 bar|
|Oxygen quality inlet||Oxygen quality inlet|
|Purity||Up to 99.9%|
|CO||< 2 ppm|
|CO2||< 150 ppm|
|Oil||< 0.05 mg/m3|